Thermal IR Inspection of 5 electrical distribution switchboards at the installation. Switchboards and Subboards are located in various different positions within each tenancy . Inspection took place following a recommendation from insurer as part of predictive maintenance program
There is a fault on the main switch of the switchboard. After taking load readings we verified the amount of electricity being drawn did not justify the heat on that cable. Electricians were scheduled to attend out of hours, at 7am, before the business opened. The main switch was replace with o unscheduled downtime. Subsequent scan revealed that the thermal exception had been rectified.
Had this not been picked up the result could have been catastrophic.